Importance of Earth Mat in Substation
The earth mats or grounding mats are used to bring the connection to the earth indoors. They usually connect through a conductor inserted within the ground port of an electrical outlet. They help in limiting the ground potential & protect against the faulty current. Earthing mat is mostly used in a place where the large fault current is to be experienced.
Electrical power systems comprise of a network of electrical elements that generate, distribute and transmit electrical energy through transmission lines. The substation grounding systems are made up of a network of conductors interconnecting the metallic parts of equipment and structures, and an arrangement of conductors buried underground. These provide an electrical connection to the earth.
In general, the earth is composed of several layers of soil at any location selected for the construction of a substation. The soil is a part of the fault circuit; therefore, a protection circuit is needed to be established. That is why the earth mats or ground mats are used to protect humans who may come in contact with this fault circuit.
How are the Earth Mats placed for substation protection?
In a Substation, Earth Mats are connected to the Following:
-The neutral point the system through its independent earth.
-Equipment framework and other non-current carrying parts of the electrical equipment in the sub-station.
-All extraneous metallic frameworks are not associated with equipment. Handle of the operating pipe.
-Fence if it is within 2 m from earth mat.
In addition to the grids below the ground level, Earthing spikes or electrodes are driven into the ground. They are electrically connected to the equipment bodies, earth grid, structures, neutrals, etc. All these together are connected to the Earthing system of the substation by several Earthing strips.
All these offer a low earth resistance which is the primary purpose of Earthing. The inter-link is made through a flat or rod conductor called an Earth Mat or Grid. It offers the surface of substation equipment a near-absolute earth potential. As a result, they help with physical protection against faulty currents. While designing an Earthing mat, the following step is taken into consideration.
If the switchyards have soil that is low in resistance, the earth resistance of the Earthing system would also be low. If the soil resistivity is high, the mesh rods are laid with closer spacing with more electrodes inserted in the ground.
- The voltage between the ground and the ground surface is not dangerous to a person during a fault condition. A person who may have to come in contact with the non-current-carrying conducting surface of the electrical system is protected during a fault condition.
- Interrupt a fault current that may flow into the Earthing mat if it is large enough to operate the protective relay. The resistance of the ground is low to allow the fault current to flow through it. Therefore, the resistance of the mat will not permit the flow of fatal current into the person’s body.
Ideally, the ground around the substations should have zero ohms resistance. There is no established standard ground resistance threshold available and is recognized by all agencies. However, the NFPA and IEEE have recommended a ground resistance value of 5.0 ohms or less. To achieve this, the substations must:
1. Have Neutrals for generators, transformers, capacitors, and reactors a connection to the earth.
2. Offer a Low-resistance path to the earth for the currents resulting from ground faults, lightning rods, surge arresters, gaps, and other devices.
3. Limit the potential differences that appear between the substation metallic objects or structures, and the ground potential rise (GPR), due to the flow of ground currents; they may pose a danger to equipment and personnel.
4. Improve the operation of the protective relay scheme to clear ground faults
5. Increase the reliability and availability of the electrical system
6. Allow the grounding of de-energized equipment during maintenance
The primary function of Earthing Mat is to provide all the above.
How do the Earth mats help in grounding?
The various applications of electricity that include ‘++’ (lighting, electromechanical conversion, telecommunications, process control, information technology, biomedical equipment, and such.) become hot by the faulty current. Workers who are involved in working with the equipment or around that area are exposed to the equipment which may also become hot due to a faulty current if there is any.
As an important part of the substation grounding system the earth mats:
- Ensure the safety of workmen against electrical shocks by keeping the touch potential and earth potential in the switchyard under any earth fault condition within safe limits.
- Provide neutral Earthing or ground connection to connect the neutrals of stat connected to transformer’s winding to earth.
- Discharge the overvoltage from overhead lightning masts or ground wires to the earth for providing a ground path for surge arresters.
- Arrange for a path to discharge the charge between phase and ground using Earthing switches.
- Provide Equipment Earthing or earth connections to structures of the substation and other non-current carrying metallic parts in the sub-station.
- Ensure the safety of personnel and the general public through touch and step potential.
Earthing mat is one of the essential parts of electrical grounding required for reducing the overall grounding resistance in substations.
Axis India Limited manufactures high conductivity copper tape, lattice earth mats to minimise the dangers of high step and touch voltages to operators in a circumstance like High Voltage switching.
Thank you for reading the blog, Axis is a leading manufacturer and supplier of Electrical Components to over 80+ Countries. To get a quote or to talk to our industry expert visit our contact us section. You can also watch our videos by our experts - click here.